- At Home
About 83,750 Thomas Lighting ceiling flush mount light fixtures have been recalled because of fire and shock hazards, according to the U.S. Consumer Product Safety Commission (CPSC).
Why it's being recalled: The fixture's socket wire insulation can degrade, leading to charged wires becoming exposed, causing electricity to pass to the metal canopy of the fixture. This poses a fire and electric shock hazard to consumers. Thomas Lighting has received 11 reports of defective fixtures which resulted in the home's Arc Fault Circuit Interrupter (AFCI) tripping. So far, no injuries have been reported.
Description: The recall involves 28 different models of ceiling flush-mounted light fixtures manufactured between June 1, 2010 through November 25, 2010 with a diameter ranging from 7.5" to 13". All affected fixtures have a round base or canopy affixed to the ceiling and a dome- or cylindrical-shaped cover. The recalled fixtures have a variety of finishes including metal and/or clear or frosted glass and contain one, two or three light bulbs. Canopies are a range of colors including white, bronze, brass (gold) and nickel. Most models have a nib in the center of the dome cover in the same color as the canopy. Although the manufacturer's name, the fixture model number and production date can be found on a printed label on the ceiling-side of the fixture's metal canopy, consumers are advised not to remove the metal canopy from the ceiling in order to access this label. For a full list of the affected models, visit the CPSC website.
Where it was sold: The fixtures were sold at electrical distributors and lighting wholesalers nationwide from July 2010 through July 2011 for between $19 and $50 as Thomas Lighting products.
Consumers should immediately stop using the light fixture, avoid direct contact with the fixture and contact Thomas Lighting to arrange for a free in-home repair of the fixtures by a qualified electrician. For additional information, contact Thomas Lighting at (800) 764-0756 between 9 a.m. and 5 p.m. ET Monday through Friday, or visit the firm's website at www.thomaslighting.com
View the full recall on the CPSC's website here.